|Automatic Regeneration for Well Water Iron and Odor|
Basic system includes automatic control valve, mineral tank ( 9" d x 48" h ), One Cubic Foot of Green Sand Plus, a round poly feeder tank ( 5 gallon - CJ7181-03 - pictured in related products ), owners basic timer set up manual ( full 5600 manual can be downloaded ). You will need to pour in gravel and Green Sand Plus with funnel, screw valve to tank, then connect inlet, outlet, and drain line. Requires 5 gpm to properly Backwash ( usually once every 2 - 3 days ). Plug into electric and set time of day. Select to Backwash once every 2nd or 3rd day. And once a month add 1 pound of Potassium Permanganate ( not include ) to the Feeder Tank. Plumbing connections are 3/4" female threaded by pass or 1" female threaded by pass ( Your Choice ). A Stainless Steel By Pass Included.
This system not recommended for Iron levels above 5 ppm or 1 ppm of Hydrogen Sulfide. Larger systems available. Please email for specifics ( include your water analysis results, please ). We will not sell this unit to you, until we are confident it will work on your water quality. Higher levels of Iron or Hydrogen Sulfide require larger tanks, or other types of treatment equipment. The Green Sand Plus media can be replaced inexpensively, when the time comes that it is necessary ( 1 - 5 years typically ).