A customer has had 2 distributor failures within a relatively short time.
This time he thinks he may have lost the majority of his resin.
Can you please shed some light on possible causes for distributors to fail.
I'd like to make sure his third one lasts longer.
* Here is what I know will effect bottom distributor life.
1 ) Too much water pressure ( over 80 psi ).
If local "city" pressure is too high, a pressure regulator should be installed before water enters the house.
2 ) Not backwashing ( regenerating ) often enough. System should regenerate
at least once every 7 days.
I've run into "metered" or "demand" systems with just one or two people and
it takes them 2 - 3 weeks to "require" a regeneration.
This is too long for the resins to be "packed" down and not "fluffed up".
Reference = Frequency of Regeneration - How Often Should Softener Recharge?
3 ) Highly Chlorinated water can break the resins down into small fragments.
These fragments get stuck in the fine slots of the bottom distributor. This
results in there being less "holes" for the water to flow through, thus
causing the pressure through the remaining holes or slots to become very
high. Eventually the pressure of the water becomes too high and the plastic
gives way. Then the larger ( normal size ) resins can get into the pipes.
Reference = Resin Replacement Guide
4 ) Too high of flow rates can be a problem. Residential size softeners (
tank diameters between 8 - 10 inches ) are made for flow rates of less than
8 gpm. And a normal home will peak around 5 - 6 gpm while filling the
laundry tub, or the bath tub. If the demand is greater than this, the system
needs to have a larger tank diameter, and a gravel under bedding should be used.
Reference RESIN Replacement Guide,
> # 1 FAQ = High Water in Brine Tank - Problem -Softener does not remove the water from my salt tank or overflow
> 5600 - difference between metered, 12 day softener valve and Backwash ONLY
> 5600 - Manual Regenerate - Cycle Times
> Adding Carbon to Resin in same Tank - Not Recommended
> Air Check - Ball seated or dropping early during the BRINE/SLOW RINSE -Autotrol 155 or 255 Series
> Alternate Drain Fitting that comes with every Hankscraft Valve
> Autotrol 155 or 255 High Water in Brine Tank - Problem No Suction or Overflowing
> Average Salt Amount Needed and Normal Water Level In Brine Tank
> Backwash Only Valve Replacement Options
> Basic Installation Guide for New Water Softener
> BIRM - How To Replace / Use in Filter Tank
> Black water into the house in the morning after it has cycled ( regenerated )
> Brine Refill problem with Fleck 5600
> Brine Suction problem or High Water in Salt tank with Clack WS1 Valve
> Brine Suction problem with Fleck 5600 or similar Hankscraft Valve
> Cabinet Model Design - Pros and Cons
> Carbon replacement - How often should you replace the carbon in a whole house unit?
> Choosing a Resin - What is the Difference
> Choosing a Softener System - Which Brand is Best?
> Clogged Injector in Iron Filter
> Dirty Brine Tank - Is there a way to clean the softener, and retain or clean the softener beads so they can be saved and reused?
> Fittings Measurements Different Then Expected ( 1/4 and 3/8 fittings )
> Fleck 2500 leak to drain - Reasons why valve is still leaking after replacing the Seals & Spacers ( 60021 )
> Fleck 2510 Valve to Tank Adapter Leak - O-rings to replace
> Fleck 3200 timer - Brine Refill Rate Explained
> Fleck 3200 timer problems - if "stalling" or not "advancing".
> Fleck 5600 - Power Head replacement - Standard in place of "L" Bracket
> Fleck Valve - Greensand application - Purple Water After Regeneration
> Fleck Valves - LEAKS out the DRAIN HOSE
> HANKSCRAFT H2O PRODUCTS and Replacement Valves
> High Water in Brine Tank - Problems and Solutions
> How and Why to use Acid Neutralizing Media Calcite and Corosex ( Magnesium Oxide )
> How does Hankscraft metered valve compare with the Fleck 5600 or the Hankscraft digital unit in terms of lasting durability
> How Long Until Water Feels Soft Again After Repair
> How To Replace Media ( Carbon, Birm, Greensand, or Calcite ) in Filter Tank
> Iron Filter, Greensand, MGS, Birm and Issues including Clogged Injector
> Low Pressure Through Softener On Chlorinated Water
> Low Pressure Through Softener On Well Water
> MediaGuard filter on Distributor Tube can cause pressure loss
> Motor Identification - How to determine Type and Part Number
> No Pressure Unless the Softener is By Passed
> Orange Sand Coming Into House
> Pressure Drop or Flow Rate reductions through a Water Softener / Filter System - Things to Consider
> Pump Pressure Low or Cycles OFF and ON ( Well Water )
> Pyrolox - How To Replace / Use in Filter Tank
> Recommendation of Fleck 5600 Econominder and Hankscraft Equivalent water softener replacement valves
- Which Brand is Best?
> Refilling when it should Sucking Water out of Salt Tank ( Brine Rinse cycle ) Fleck Valve
> Relieving Pressure Fleck 5600 Valve
> Salt is Not Going Down.
What could cause this problem?
> Sears and GE Smartwater - Water Not Soft - Distributor Oring problem and solution
> Sediment filter ahead of the softener - When, Why, and Which one.
> STUCK Valve Fleck 5600 Rebuild Guide
> Tools Kit 60135-2510 for Service 1500, 2500, 2510 Seals & Spacers
> Trouble Shooting Guide for the Fleck 5600 and 5600 Econominder Valve
> Whole House Carbon Filter - Which is best for city water?
> Why Gravel is Not Needed in Residential Size Water Softener