The amount of salt needed to properly recharge a water softener is mostly based on the amount of resins being recharged.
3/4 cu.ft. resin = 6 - 9 lbs.
1 cu.ft. resin = 8 - 10 lbs.
1.5 cu.ft resin = 12 - 15 lbs.
9 lbs for 8 - 9 inch tanks,
and 12 lbs. of 10" tanks is average.
If there is a lot of iron ( over 2 ppm )
or if the water is really hard ( over 30 grains ),
then 2 - 4 lbs. extra should be used.
So, an average residential system will use 6 - 12 lbs of salt per regeneration at least once a week. Very hard water, or water high in iron, may require regenerating every 2 or 3 days. The result is you will be using at least 30 - 40 lbs. of salt per month if hardness is not too high, or amount of water used low.
Well water ( usually very hard and often containing iron ) will commonly require using 80 - 120 lbs. of salt per month.
Simply multiply the pounds of salt per regeneration times the number of regenerations in a month to calculate your monthly average usage.
P.S. If you run out of Salt, don't expect to have soft water after a few days. And it may take more than one regeneration to get the water feeling soft again once you've added salt.
I recommend keeping the salt level above the water level in your Brine Tank.
When you start seeing the water level ( normally between 6 - 12 inches ) then it's time to think about adding more salt ( 40 - 120 lbs. ).
Does it matter which type of salt is used? Pellets or solar salt crystals? Is one better than the other?
Either will work.
the solar salt crystals as they dissolve 100%, as opposed to the
Pellets that leave an un-dissolved residue in the bottom of the brine
tank. And this residue builds up until it clogs the flow of the brine
water in and especially, out of the salt tank, requiring that the tank
be dumped, emptied, and re-filled with new salt ( plus 4 gallons new
water ) every 1 - 2 years on average.
In simplest terms:
The Control Valve should be adding 3 - 4 gallons of water at the end of regeneration process ( Brine Refill ). A level of 6 - 12 inches, depending on the amount of salt in the brine tank, and the shape of the brine tank ( square or round ).
During Brine Rinse ( long 50 minute cycle ), the valve should suck out the 3 - 4 gallons of water in about 20 minutes ( less than 1/4 gpm ), and once water level drops to the last couple of inches of the salt tank, the "air check" will close off, to prevent any "air" from getting sucked into the Valve. The Brine Rinse ( slow suction and slow rinse ) will continue for another 30 minutes, as it slowly rinses the salt water through the Resin Tank, allowing it to Recharge the Resin beads.
How A Water Softener Works
Sodium Levels in Water when Softened
> # 1 FAQ = High Water in Brine Tank - Problem -Softener does not remove the water from my salt tank or overflow
> Links to Other Websites
> Distributor Failure in Bottom of Resin Tank
> How and Why to use Acid Neutralizing Media Calcite and Corosex ( Magnesium Oxide )
> Low Pressure Through Softener On Chlorinated Water
> Low Pressure Through Softener On Well Water
> No Pressure Unless the Softener is By Passed
> How a water softener actually works and why does it feel slimy
> Salt Usage In Water Softening
> No Salt Systems for Water Softening
> Dishwasher Glassware Etching Cause Explained
> Air in water lines after Softener Regenerates
> Trouble Shooting Guide for the Fleck 5600 and 5600 Econominder Valve
> STUCK Valve Fleck 5600 Rebuild Guide
> Clogged Injector in Iron Filter
> Common Water Problems
> ECO - Friendly Alternative to SALT Softeners
> How do you determine if you actually need a softener?
> How do you put a softener out of service without damaging it?
> How Long Until Water Feels Soft Again After Repair
> Hydrogen Sulfide levels affected by amount of water used and the ground water table
> Will a Water Softener remove the iron from my water?
> Iron Staining and my Water Softener seems to be working okay, Why is that?
> Odor - Sulfur (Hydrogen Sulfide) in your water
> I have a Water Softener, but I still have odor in my water.
Why is that?
> Orange Sand Coming Into House
> Refilling when it should Sucking Water out of Salt Tank ( Brine Rinse cycle ) Fleck Valve
> Salt is Not Going Down.
What could cause this problem?
> Salty Water Taste in the Morning
> Sears and GE Smartwater - Water Not Soft - Distributor Oring problem and solution
> High Water in Brine Tank - Problems and Solutions
> Sodium in the Water Softening
> What Brine ( Salt ) Setting Amount to Use?
> Will a Water Softener make my water safe to drink?
> Stains in Laundry - several possible causes
> Tools Kit 60135-2510 for Service 1500, 2500, 2510 Seals & Spacers
> Iron Filter, Greensand, MGS, Birm and Issues including Clogged Injector
> Looking for someone to Service My Water Softner ( Softener ) in my area.
> 5600 - Manual Regenerate - Cycle Times
> Pump Pressure Low or Cycles OFF and ON ( Well Water )
> Brine Suction problem with Fleck 5600
> Brine Refill problem with Fleck 5600
> Relieving Pressure Fleck 5600 Valve
> Stinky - Rotten Egg - Odor
> Sodium Levels in Water when Softened
> Air Check inside Brine Tank can becomes Stuck or Water Logged
> Aerator Use and Cleaning Q & A
> Air Check - Ball seated or dropping early during the BRINE/SLOW RINSE portion on the 155 or 255 Series Valve
> Brine Valve Replacement in Salt tank ( with Float Shut Off )
> UV for Water Purification - Does it Work?
> Why Gravel is Not Needed in Residential Size Water Softener
> 5600 - difference between metered, 12 day softener valve and Backwash ONLY
> Frequency of Regeneration - How Often Should Softener Recharge?
> Fittings Measurements Different Then Expected ( 1/4 and 3/8 fittings )
> Choosing a Resin - What is the Difference
> Basic Installation Guide for New Water Softener
> Which is better or cheaper... Powdered Resin Cleaners or Res-Up Liquid?
> Fleck Valve - Greensand application - Purple Water After Regeneration
> Choosing a Softener System - Which Brand is Best?
> Sediment filter ahead of the softener - When, Why, and Which one.
> Brine Tank Assembly - Questions, Answers, Video Link
> Brine Suction problem or High Water in Salt tank with Clack WS1 Valve
> ChemTech and Pulsafeeder chlorine solution pumps
> Fleck 3200 timer problems - if "stalling" or not "advancing".
> Potassium Chloride - Substitute for Salt ( Sodium Chloride )
> Pressure Drop or Flow Rate reductions through a Water Softener / Filter System - Things to Consider
> Fleck 5600 - Power Head replacement - Standard in place of "L" Bracket
> HANKSCRAFT H2O PRODUCTS and Replacement Valves