To regenerate the Fleck 5600 valve used on softener, without working timer motor. The following steps are involved in regeneration: Time to leave in each cycle Regen - none, valve does nothing in that position Rinse - none really, just move control knob until you hear the water flowing out the drain, and you'll be in Backwash cycle. Backwash - 10 minutes Brine rinse - 50 minutes ( and no less, as this is the most critical cycle ) * NOTE: Y ou have to move just past the words "Brine Rinse" before the Suction cycle starts ( and the Brine Valve Piston is pushed down / opened in the rear of control ) . Rapid rinse - 10 minutes Settle rinse - 5 minutes Brine refill - until it refills back to normal water level in brine tank ( 6 - 16 minutes ).
The 5600 Filter Valves using black top filter piston ( PN 60102-10 ), and if BACKWASH ONLY ( not connected to any type of "feeder" tank for potassium, salt, or chlorine) you would SKIP the Brine Rinse and Brine Refill.
Also the Backwash time would be increased to 15 minutes ( also the Rapid Rinse cycle to 15 minutes ). See more on the Differences in Main Piston Assemblies ( 60102-00, -10, -20 ). Also this Short Video on Manually cycling the Fleck 5600,
leave in backwash
leave in brine rinse
# 1 FAQ = High Water in Brine Tank - Problem -Softener does not remove the water from my salt tank or overflow
> Distributor Failure in Bottom of Resin Tank
> Low Pressure Through Softener On Chlorinated Water
> Low Pressure Through Softener On Well Water
> No Pressure Unless the Softener is By Passed
> Average Salt Amount Needed and Normal Water Level In Brine Tank
> Trouble Shooting Guide for the Fleck 5600 and 5600 Econominder Valve
> STUCK Valve Fleck 5600 Rebuild Guide
> Clogged Injector in Iron Filter
> Fleck 5600 parts rebuild with or without replacing the Timer Motor
> Fleck 5600 Still Getting Stuck After Replacing the Pistons and Seals Kit
> How Long Until Water Feels Soft Again After Repair
> How to Set Meter without the People or Hardness Labels on Fleck Econominder Valves
> New Timer Motor 18743 kicks the unit into 'REGEN', but that's as far as it will go.
> Orange Sand Coming Into House
> Refilling when it should Sucking Water out of Salt Tank ( Brine Rinse cycle ) Fleck Valve
> Program Wheel replacement on Fleck 5600 Valve
> Salt is Not Going Down.
What could cause this problem?
> Sears and GE Smartwater - Water Not Soft - Distributor Oring problem and solution
> High Water in Brine Tank - Problems and Solutions
> Brine Failure on ONE Tank Only - 9000 / 9100 Twin Alternating Valve
> Water Flowing to Salt Tank after replacing
Brine Valve Piston Assembly Fleck part 60032
> Fleck Valve Leaking to Drain Continuously
> Switches Breaking Fleck 9000, 9100, or 9500 Valves
> Tools Kit 60135-2510 for Service 1500, 2500, 2510 Seals & Spacers
> Iron Filter, Greensand, MGS, Birm and Issues including Clogged Injector
> Continually Cycling ( Regenerating ) Problem - Fleck 9000, 9100, or 9500 Valve
> 5600 Piston Assembly Types - Softener - Filter - Low Water
> Pump Pressure Low or Cycles OFF and ON ( Well Water )
> Brine Suction problem with Fleck 5600 or similar Hankscraft Valve
> Brine Refill problem with Fleck 5600
> Relieving Pressure Fleck 5600 Valve
> Air Check - Ball seated or dropping early during the BRINE/SLOW RINSE portion on the 155 or 255 Series Valve
> Fleck 3600 Valve Obsolete but can be Replaced
> Brine Cam Gear Sheared and Broken Off Plastic Housing Inside
> Meter - Checking the Operation of the Fleck 3/4" Meter Cover
> Meter - Cover Replaced, but Still not working..
> Why Gravel is Not Needed in Residential Size Water Softener
> 5600 - difference between metered, 12 day softener valve and Backwash ONLY
> Photos 5600SE, 5600SXT, 6600, and 6700 - Which Kit or Pistons for these Electronic Timers
> Fleck 5600 SE or SXT are NOT the same as Mechanical Versions of Fleck 5600
> Fleck 5600 SE or SXT are NOT Recommended over Mechanical Fleck 5600
> Fleck SE or SXT Error Codes
> Fittings Measurements Different Then Expected ( 1/4 and 3/8 fittings )
> Meter - Leak at Cable Connection Hole on the Fleck 3/4" Meter Cover
> Fleck 24 volt AC transformer - Which to Choose
> Fleck Valve - Greensand application - Purple Water After Regeneration
> Brine Suction problem or High Water in Salt tank with Clack WS1 Valve
> BLFC button question 0.25 versus 0.50 gpm with Fleck
> Fleck 3200 timer problems - if "stalling" or not "advancing".
> Pressure Drop or Flow Rate reductions through a Water Softener / Filter System - Things to Consider
> Fleck Yoke Dimensions - Internal, External and Center To Center
> Fleck 5600 - Power Head replacement - Standard in place of "L" Bracket
> Fleck Piston 24507 - Fleck Model 5656 / 5665 UF are NOT the same as Mechanical Versions of Fleck 5600
> HANKSCRAFT H2O PRODUCTS and Replacement Valves
> Valve Replacements - Fleck 8500 / Twinflo 100E with Fleck 9100 or a single valve / tank option
> Fleck 2500 leak to drain - Reasons why valve is still leaking after replacing the Seals & Spacers ( 60021 )
> Alternate Drain Fitting that comes with every Hankscraft Valve
> Turbulator - Why Would Someone Use This Over A Standard Bottom Distributor Basket / Riser Pipe?